An urgent warning has been issued by the Building Engineering Services Association (BESA) about a potential fire safety weakness in a large number of building ventilation systems.
The UK’s leading trade organisation for building engineering services contractors has issued an interim technical bulletin (VH001) ahead of a full update of its industry guidance for the ‘Installation of Fire Dampers and Smoke Dampers’ (DW145) which is due for launch at the Association’s National Conference in October.
BESA said it was taking the unusual step of producing an interim announcement because of the urgent nature of the problem after annual inspections carried out by maintenance contractors found that “a huge number of dampers” had been incorrectly installed.
Head of Technical Graeme Fox explained that many did not comply with manufacturers’ instructions and needed remedial action “without delay”.
He added: “We have been alerted to the very dangerous practice of using self-drilling ‘tek’ screws which do not melt when temperatures rise during a building fire. This means spring-loaded dampers will not be released to contain the spread of fire within the zone and ensure the integrity of the fire stopping measure.”
“Dampers must be secured by fusible fixings that allow the duct to break away otherwise the collapsing duct could pull the damper out of place and break the seal between the fire zones.”
BESA’s technical committee sanctioned the technical bulletin, which is freely available on the Association’s website, to give contractors the information and appropriate terminology to alert clients to this potentially life-threatening problem.
The bulletin also updates the guidance and statutory requirements covering installation, testing and maintenance of fire dampers and smoke dampers including clients’ legal obligations to ensure their fire safety systems remain fit for purpose in line with the Regulatory Reform (Fire Safety) Order 2005 for England and Wales and the Fire Safety (Scotland) Regulations 2006.
It outlines the crucial role played by the penetration seal in ensuring the overall fire stopping integrity of an installation, the importance of maintenance teams being able to find and access dampers for testing and repair, and the need for designers and installers to seek expert advice from damper manufacturers.
Fox continued: “While this is clearly a very worrying situation, we can take some reassurance from the fact that this problem is being brought to our attention by the increasing frequency of fire damper inspections and tests as awareness grows of this extremely important issue.
“We would urge contractors to alert their clients immediately so all the necessary checks and repairs can be carried out.”
Creating a positive visitor experience in a Hybrid world of work
While some personnel are finally returning to the office – the great majority of organisations (up to 83 per cent) anticipate a hybrid mix of on-premises and working from home to continue for the foreseeable future.
This means that when it comes to providing access to the workplace, where once it was simply enough to maintain a welcoming reception for visitors, organisations today must also keep a close eye on access permissions in real-time to keep buildings safe and secure while ensuring they comply with compliance.
Pitney Bowes Smart Access Management in association with FMJ has produced a new White Paper which explains how to create a welcoming, actively managed environment for authorised people.
It explains how new Smart Access Management™ (SAM) delivers a complete, real-time and data-driven view of all your people, visitors and contractors, to help give you greater control and visibility.
To download the white paper click here.